Powmr 230VAC 4KW Battery PV 18A 360VDC Hybrid PV Inverter With Parallel 6 Units
Powmr Battery 230VAC 4KW PV 18A 360VDCHybrid PV Inverter With Parallel 6 Units
POW-SUPER-4KW-6P can operate up to 6 units in parrallel simultaneously and generate rating output power up to 24KW. Adjustability of charging current for different batteries, its AC/solar charger is upgraded to 80A. With dual AC inputs, it`s compatible with both utility and generator, so you don`t have to worry about interruption of power supply.
- Brand: Powmr
- Product Model: POW-SUPER-4KW-6P
- Parrallel operation up to 6 units
- Pure sine wave output
- Self-consumption and Feed-in to the grid
- Programmable supply priority for PV,Battery or Grid
- User-adjustable battery charing current suits different types of batteries
- Programmable multiple operation modes: Grid-tie,off-grid and grid-tie with backup
- Accept dual AC inputs:Utility and Generator compatible
- Built-in emergent power supply port for emergent lighting or loads
- Multiple Communication for USB,Modbus and SNMP
- Monitoring software for real-tiem status display and control
- Enhanced AC/Solar charger to 80A
The cable size of each inverter is shown below
Recommended battery cable and terminal size for each inverter:
WARNING: Be sure the length of all battery cables is the same. Otherwise, there will be voltage difference between inverter and battery and it might cause mal-function of the working inverters in parallel.
Recommended AC input and output cable size for each inverter:
You need to connect the cables of each inverter together. Take the battery cables for example: You need to use a connector or bus-bar as a joint to connect the battery cables together, and then connect it to the battery terminal. The cable size used from joint to battery should be X times of cable size in the tables above. “X” indicates the number of inverters connected in parallel.
Regarding cable size of AC input and output, please also follow the same principle.
This hybrid PV inverter can provide power to connected loads by utilizing PV power, utility power and battery power.
Depending on different power situations, this hybrid inverter is designed to generate continuous power from PV solar modules (solar panels), battery, and the utility. When MPP input voltage of PV modules is within acceptable range (see specification for the details), this inverter is able to generate power to feed the grid (utility) and charge battery. This inverter is only compatible with PV module types of single crystalline and poly crystalline.
Do not connect any PV array types other than these two types of PV modules to the inverter. Do not connect the positive or negative terminal of the solar panel to the ground.
Unpacking & Overview
- PV connectors
- AC output connectors (Load connection)
- Battery connectors
- AC Grid connectors
- Dry contact
- USB communication port
- RS-232 communication port
- Intelligent slot
- Emergency power off (EPO)
- EMS port
- DC Switch
- Generator connectors
- Parallel communication ports
- Current sharing ports
- LCD display panel (Please check section 10 for detailed LCD operation)
- Operation buttons
The inverter is built in several communication ports and also a slot for alternative communication interfaces in order to connect it with a PC for installing corresponding software. This intelligent slot is suitable to install the software with SNMP card and Modbus card. Follow the procedure below to connect communication wiring and install the software.
Please install monitoring software in your computer. Detailed information is listed in the following chapter. After software is installed, you may initial the monitoring software and retrieve data through communication port.
Application with Energy Meter
With Modbus card II and energy meter, hybrid inverter can be easily integrated into the existing household system. For details please refer to Modbus card II manual.
Note: this application is only valid for Grid-Tie with Backup II mode
Equipped with Modbus card II, hybrid inverter is connected to energy meter with RS485 communication port. It’s to arrange self-consumption via Modbus card to control power generation and battery charging of the inverter.
This inverter can be used in parallel with maximum 6 units. The supported maximum output power is 24KW/24KVA.
You will find the following items in the package:
Mounting the Unit
No reviews found